AGS-11/1 Aerosol Fire Extinguisher
|2,2 m3||8 sec||0,6 kg
DESIGN: AGS-11/1 aerosol fire extinguisher generate dry aerosol cloud which extinguishes fire upon reaching necessary concentration in protected volume. AGS-11/1 aerosol fire extinguisher has steel cylinder body with nozzle gap around the side surface of the body. Despite compact size AGS-11/1 aerosol fire extinguisher has protected volume 2.2 m3. Outer aerosol stream temperature is lowered by air cooling.
OPERATION: Electric signal activates the starter installed inside aerosol fire extinguisher which ignites the aerosol forming cartridge. Aerosol cartridge produce large volume of fire extinguishing aerosol streaming through the cooling layer and coming out of fire extinguisher through the nozzles. Thanks to its unique properties aerosol stops the fire and prevents following reignition.
APPLICATION: AGS-11/1 is recommended for the protection of electronic equipment, electric cabinets, high-voltage power installations, various stationery or moving high-frequency devices, as well as vehicles, since it corresponds to the requirements for vibration loads on railway, road and air transport.
WARRANTY: Manufacturer guarantees that fire extinguisher conforms to declared technical specs and standards if the consumer strictly follows the Instruction Manual.
Warranty period – 18 months
Operation life – 5 years
Service life – 10 years
Basic specs Fire classes Protected volume 2,2 m3 Operating time 6 - 10 sec Net Weight of extinguisher 0,61 kg Net Weight of aerosol forming compound 0,11 kg Overall dimensions Diameter 124 mm Height 53 mm Starter type Internal UZ-7.5 Starter electric impedance 7,5 Ohm Starting impulse minimum current 1A Starting impulse voltage 12 – 24 V Starting impulse duration Not less than 1,5 sec Startup delay < 2,5 sec Operating conditions Temperature ± 50 °С Humidity up to 98 % Acceleration at frequency range up to 100 Hz 0,5g
Certificates available on request. Please complete the form below.
Manual is available on request. Please complete the form below.